Fm200 Gas Cylinder Hfc-227Ea Extinguishing System Gas Sprinkler
|2||Scale of Protective region for one zone||area:max single-zone is 800m2 volume:max single-zone is 3600m3|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||5.3Mpa||8.0Mpa|
|9||min working pressure||4.2Mpa||4.6Mpa|
Fm200(htc-227ea) is a kind of colorless and tasteless
and non-corrosive and electricity-insulating gas without residue
and pollution after extinguishing. And ODP of it is zero. It is a
friendly-environment gas to be used for extinguishing. Also,
because of such feature, it can be used in special place where
electrical fire is easy to happen.
Management of Multiple zones is also in the safe
control of the whole system. We can use one system to protect
multiple zones through selective valves. It can let the whole
system alternative aiming at different protective zone. Agent can
be discharged into where the fire happens. It will be very
efficient to put out fire in short time. One thing that need to
mention, is that a little room should be prepare to be as storage
space for the whole system.
Electronic computer room, a data processing center,
telecommunications facilities, process control, industrial
equipment, library, museum and art gallery, clean room, anechoic
chamber, emergency power facilities, flammable liquid storage area,
The place where the fire is easy to happen, like
paint-spraying production line, aging-electrical equipment, rolling
machine, printing machine, oil switch, oil immersed transformer,
melt impregnating tank, tank, large generators, drying equipment,
cement production process of pulverized coal, and the ship's engine
room, cargo hold, etc.
HFC 227 Fire Extinguishing System piped with 150L
containers is mainly composed by three parts. Extinguishing devices
and pipe fittings and electrical accessories.
1. Mechanical parts: cylinder with container valve, frame for
cylinder group, driving cylinder, frame for driving device, high
pressure hose etc. It is mainly used for storing fm200 agent.
2. Electrical parts: smoke detector, heat detector, bell etc.
3. Pipe fittings: conduit, connector, elbow, flange etc.
These integrated three parts will be efficient to
detect and supervise and alarm and extinguish fire automatically.
Here attached below is complete composition of whole